For desalination of softened drinking water according to drinking water regulations (free chlorine not detectable).
Very high permeate recovery up to 90 % due to additional concentrate stage and high salt rejection up to 98.5 %. Short ROI/ payback period (mostly < 1 year) through savings in water and waste water. Concentrate flushing device KSE and connection kit ARA already integrated.
membranes: 4040 x 4, 8040 x 3
Up to 30% energy savings due to high pressure pump with frequency converter.
Skid mounted, complete unite
RO 5000 controller
Recovery from 85% to 90%
Salt rejection percentage: min. 98,5%
Working pressure: 15 to 18,5 bar (depending on type)
Inlet pressure: 2 to 4 bar
Voltage: 3 x 380V
Analogue flow meters
Incl. concentrate rinsing
Incl. connector kit for manual cleaning set
Water saving system through additional concentrate stage: permeate yield up to 90%
High salt rejection rate: 98,5%
Very low energy consumption KR/FU: -30%
ROI/ payback period: < 1 year through cost savings in water, waste water and energy
ARA - CONNECTION KIT FOR MANUAL CLEANING UNIT
Ball valves for the connection of a manual cleaning unit e.g. for acid or alkali cleaning of the RO membrane.
Easier to make the cleaning as the pipings do not need to be disconnected first.
Economy of time for making the cleaning
*The unit is designed for a maximum TDS of 1,000 mg/l, a max. SiO2-concentration of 10 mg/l, a water temperature of 15°C, a maximum colloidal index of 3 and no permeate back pressure. Under these conditions, the unit still reaches design permeate flow after three years of operation. The permeate recovery depends on the raw water quality and the type of pre-treatment.